|Type of design||Metal Oxide Varistor||
|Type of Design SPD||Metal Oxide Varistor|
|Maximum Current L-N||20,000 AMPS|
|Maximum Joules L-N||800 Joules|
|Tested to||NEMA C62.11|
|Category B & C and Type 1 & 2|
|Leads||36" #12 THHN|
|Response Time||5 nanoseconds|
|Locknut and Washer furnished||1/2" Nipple Washer & Locknut|
|DELTA LIGHTNING ARRESTORS,™ INC.||
P.O. BOX 750
BIG SPRING, TX 79721
Fasten arrestor in place. Use a Delta mounting bracket, part # MB, a pipe strap, or a knockout hole. Connect the black wires to the hot lines at any convenience point load-side of an existing fuse or circuit breaker. Connect the white wire to an existing ground system, the grounded metal frame work of the equipment to be protected, or make a ground source per NEC Article 250.
For DC Installation connect red wire to positive, black wire to negative and green wire to ground. Electrical work is hazardous. Bad connections can result in fire, injury or death. Installation must only be done by qualified electricians.
In the event that a lightning discharge is so powerful that something has to be destroyed, the arrestor will take the damage. When sufficient heat and stress causes failure, a one inch hole will open at the bottom of the enclosure. Hot silica and plastic bits will be expelled. Installing the arrestor in any approved electrical box will prevent accidental contact with a damaged unit.
Please give us your feedback on our website.